Over the years, aggressive water or constant use can cause your water pipes to develop leaks. VIP Plumbing Inc. has the experience necessary to quickly identify the source of your leak and repair it.
Whether your piping is copper, galvanized, plastic, or anything else, in Cleveland, OH, VIP Plumbing Inc. is the one to call.
Replaced 6' of copper water line to repair leak.
East 45th Street Suite #200 CLEVELAND, OH
Leaking water pipe in basement. Shut off water to house. Removed 1 1/2'x 3/4" CPVC and 3/4 shut-off valve. Installed new 3/4 ' CPVC valve, pipe and coupling. Recharged water to house.
Scottwood CLEVELAND, OH
Pipe burst in kitchen ceiling from bathroom above. Customer removed ceiling area to provide access. Pulled toilet to cut out 6' of cast iron, sanitary tee and 3' of 4"vent. Removed galvanized tub drains, lav drains and vent. 20' total. Repaired in PVC. Installed new 3"closet bend and 1 sanitary tee. Piped tub and lav sink in 1 1/2" PVC. Set toilet. Installed new P-Trap.
Montrose Ave. CLEVELAND, OH
Pulled toilet. Founf improper connection of 4"PVC to 4" Cast Iron. Broke 2'x6' flooing to expose 4" sewer line. Installed new SCH 40PVC. Gravel and concrete patch.
Superior Ave. CLEVELAND, OH
Found seven total leaks on gas piping inside of the home. Three leaks were at the water heater. Bad threads on nipples and a leaking shut off valve. Four of the leaks on the shut off valve for the gas grill and piping going to the outside. Replaced the union and shut off valve on the furnace.
Kimerly Drive CLEVELAND, OH
Install a new washer in the back hose bib. Could not fully fix and the customer was aware of this possibility before I started. Gave estimate to install a new Legend 1/4 turn frost free hose bib.
McCracken Blvd CLEVELAND, OH
Tested 3/4 Wilkins 950XL double check Shut off valve - Passed #1 Check - Passed 1.4 #2 Check - Passed 2.6
Turney Rd. CLEVELAND, OH