Rheem 22V40F1 Gas Water Heater
Installed a standard 40 gallon water heater with all the proper connections. Removed old water heater from the job site as well. Installed a Rheem 22V40-F1 40 gallon standard gas water heater.
Temple Avenue MAYFIELD HEIGHTS, OH
InSinkErator Essential Garbage Disposer
Replaced a Waste King Disposal with a In Sink Erator Pro Essential $$570.00 8 yr warranty, multi grind, auto reverse, sound seal 3/4hp Serial #09111519090
Pepper Creek MAYFIELD HEIGHTS, OH
Rinnai R85i Tankless Water Heater
Called out to diagnose a problem with a Rinnai tankless water heater.. Cleaned flame sensor rod and incoming water screen. Unit would not stay lit. May arrangement to return on Monday because she had to go to work. On Monday we returned to check the gas pressure. Was told on Monday that the furnace was also now not working. Unit had been installed for a few years and had always worked fine. Found that when ever the unit would call for gas the pressure would drop down to no pressure. Took the incoming line off of the gas meter and opened the lock stop to find the gas would give a big puff and go down to nothing. There is a problem with the incoming gas line. Recommend she call Dominion gas because they would repair the service line for free.
Croyden road MAYFIELD HEIGHTS, OH
Navien NR-240A Condensing Tankless Water Heater W/ Circ
Removed two 50 gallon power vent water heaters and install a Navien NR240A-NG. We reused the 3 PVC vent pipes from the water heaters to vent the Navien unit. Mounted new unit to block wall. Removed both old water heaters from the home. Navien Model NR-240A-NG Serial #9545-20100205-2110
Settlers Ln. MAYFIELD HEIGHTS, OH
Installed a new Kohler almond seat on the powder room toilet. Removed master bath toilet and ran sewer camera through the drain. Found toilet paper sitting in the first 8-10 feet of the 3 line. Pushed the camera through the cast iron line several times to break up the toilet paper sitting in the line. Flushed with water as we worked the camera back and forth until the line was cleared. Suggested holding the handle down when you flush this toilet to put as much water as possible through the line to carry the paper away. Line pretty much has rough edges and build up through out the inside of the cast iron line. This maybe catching some of the paper and causing a build up. Reset the toilet after using the camera then caulked the toilet to the floor.
Three Village Drive MAYFIELD HEIGHTS, OH
American Standard Plumbing bath general
- Technician pulled out old toilet in 2nd. floor, kids bath, at the top of the stairs. - Installed a new American Standard Cadet 3 toilet, with a new wax seal, t-bolts and seat.
Cedar Rd. MAYFIELD HEIGHTS, OH